Today when specific shielded facilities are designed the construction materials and shields should meet a range of fire safety requirements. A composite coating on the basis of a water-based fire-resistant paint filled with shungite nanopowder can be applied onto walls, floors, ceilings and other surfaces in the shielded areas to reduce electromagnetic radiation and simultaneously to ensure fire safety. Shungite is a mineral with multilayer carbon fullerene globules which diameter is 10–30 nm. Due to the high conductivity shungite is able to weaken electromagnetic radiation. A coating made of shungite-containing paint on a cellulose substrate was subjected to the open flame under the temperature of 1700° C for 3 minutes and 40 seconds. That resulted in the formation of insulating foam layer without mechanical damage of the substrate. The XRD diffraction analysis of the powder obtained in the process of flame influence on the coating showed the formation of the such substances as orthoclase, barite, rutile, etc. Carbon contained in shungit and used as a filler for the fireproof paint wasn’t detected. This fact indicates carbon oxidation as the result of its burning out. The shielding efficiency of the composite coating after open flame exposure was measured for the frequency range 8…12 GHz with the use of the panoramic attenuation meter and voltage standing wave ratio meter YA2R-67-61 with a sweep generator and waveguides. After that the reflection and transmission coefficients were calculated. The results of measurements and calculations showed decrease of the reflection and transmission coefficients due to conductivity decrease and dielectric losses changes of the composite coating provided by silica content increase and carbon percentage decrease.
Full Text Here